An expert who has achieved level 2 by getting 100 points
An expert that got 5 achievements.
An expert whose answer got voted for 20 times.
An expert who has written 20 answers of more than 400 characters.
Re: panel reads lp error code
Loss of refrigerant, bad motor for the fan clean the coils and unit as described in the manual. Here is a manual from the Hayward website or here http://www.haywardnet.com/products/manuals/pdfs/Manual122.pdf.
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
TE error code stands for thermistor error. You have to remove the front panel and ohm out the heating element. If you have continuity most likely it will be fine. There is a thermistor located next to the heating element that will probably need to be replaced. LG's are the only machine besides GE ref's that I have ever seen thermistors go bad on. There is probably an ohm reading you should get through the thermistor but unless you have an analog meter or a fluke most standard digitals wont read into mega-ohms. Removing the front panel is model specific. But i can tell you the spring around the front boot (drum gasket) needs to be removed and there will be some hidden screws at the bottom by the pump where the access panel is located.
I happen to work for Rome Industries and can help you out. The "LP" code on your control board represents "Low Pressure". This is referring to the refrigerant pressure within the unit. The unit is equipped with a low pressure safety switch that when activated shuts the unit down. This could be caused by a refrigeration leak, a stuck thermal expansion valve, or even a faulty pressure switch. If you live within the state of Florida contact Rome Industries and you will receive a free of charge service call including parts and labor as long as your unit is under warranty. If your outside of the state please contact your dealer to handle the claim. Have a good day.