Question about Airtemp B7D18E2A Air Conditioner
Tripping can be due to over current drawn by the compressor .This can happen due to lower voltage prevailing during that period (due to several other electrical appliances being connected on the same circuit etc).The condensing unit may be accidentally covered by an obstruction (eg cloth, carpets, polythene film etc).also it can happen due to the out door unit (condesing unit) fans not working .Check the cool gas line from evaporator(cooling coil) to the (out door ) condensing unit.If this with an ice covering check your return air filter for excess dirt and correct it. ask the service man for the running current reading he got and compare it with that on the name plate ..Best you ask him to fix ammeter and take readings at regular intervals through out the day.That will give an indication.The circuit breaker itself may be defective.The amp test above will tell you that too.
Posted on Jul 05, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 31, 2015 | Air Tools & Compressors
Feb 04, 2011 | Heating & Cooling
Nov 26, 2010 | Proform 785 CS Personal Trainer Treadmill
Apr 11, 2010 | Danby DMW112 Microwave Oven
Jan 03, 2010 | Dayton D-F79 Electric Space Heater- the...
Jun 05, 2008 | LG L1004R Air Conditioner
May 23, 2018 | Heating & Cooling
35 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: