Question about LG Heating & Cooling
LG under ceiling air conditioner 410 inverter 36000 BTU Model number AUUW368D ERROR CODE: 6 red blinks and 4 green blinks
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This alarm state is a CH 06 alarm.
Indication for the Indoor unit pipe temperature sensor (thermister) not plugged in or out of calibration.
This alarm will also occur when the unit gas charge is to low and the indoor unit temperature reached a temperature of -5°C for longer that 30 sec. It will switch the machine off.
Posted on Mar 22, 2010
Tips for a great answer:
Dec 05, 2015 | Heating & Cooling
Jul 12, 2015 | LG LMN096HVT WaMounted Mini Split Indoor...
Nov 05, 2011 | LG LM360CE 36000 BTU Cooling Only Tri Zone...
Jan 01, 2011 | LG Heating & Cooling
Aug 23, 2010 | Carrier 38CKC036 Air Conditioner
Nov 29, 2009 | LG Heating & Cooling
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
318 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: