Question about Sanyo Split System Air Conditioner
D25 code : Check power supply voltage to the outdoor unit is correct (1ph ?220 Vac ±10% or 3ph ?380 Vac ±10%). If OK, check fuses, if fuses are OK replace outdoor main PCB
compressor seized. Check compressor windings all equal resistance 1 to 4 Ohms, check to earth 50 MOhm minimum, check run current and Inverter outputs
Posted on Jan 04, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 03, 2011 | Ruud Heating & Cooling
Jun 06, 2011 | Heating & Cooling
Mar 22, 2011 | Heating & Cooling
Jun 25, 2010 | Heating & Cooling
Sep 26, 2009 | Goodman CLQ36AR49 Air Conditioner
Jul 07, 2009 | Heating & Cooling
Jan 09, 2009 | Friedrich QuietMaster Electronic SS12J30D...
May 12, 2008 | Heating & Cooling
Aug 31, 2007 | Mitsubishi MSH09TW Air Conditioner
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
235 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: