Question about Goodman Heating & Cooling
On the panel with the wiring diagram, there is an error code chart. I think 3 flashes is a pressure switch problem. Check your air filter, condensate pump or hoses. Check the small hoses going to the pressure switch, check your air intake and exhaust vents. Remove any moisture or debris. Make sure all venting pitches back to the heating system and no low spots are holding water.
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 12, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Mar 01, 2013 | Lennox Heating & Cooling
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Sep 18, 2011 | Goodman GMS90703BXA Heater
Jan 10, 2010 | Goodman GDS80703ANA Open Flame Mid-Size...
Dec 07, 2009 | Goodman Furnace Draft Inducer Blower ...
Jun 02, 2009 | Goodman GMS90703BXA Heater
433 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: