Question about Mitsubishi MSY-A24NA Air Conditioner
Cold air coming out condenser, doesn't drip outside and not cold inside?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check your coils for ice, check your breaker and fuses for condensing unit, and is your condensing fan running? If not, you either have a bad fan motor or capicitor. After you hit the button, and wait for it to time out, (you should hear a click) take a butter knife, and spin the fan if it is not moving. If the fan start spinning by itself after your assistance, you have a bad capacitor
Posted on Jan 29, 2009
It sounds like you have a unit called a heat pump. When a heat pump unit is in cooling mode the outside unit blows hot air and the inside unit blows cold air. If the outside unit is blowing cold then the indoor unit is most likely blowing room temperature or warm air. It sounds like the thermostat could be controlling incorrectly or you could have a failed reversing valve which is the device that switches the unit from heating to cooling mode.
Posted on Jun 02, 2009
If you have a heat pump probably there's a wrong connectionin the thermostat, but if is not a heat pump ,the compresor is not working or the unit leaked all the refrigerant.
Posted on Aug 30, 2009
Testimonial: "thank you, we have had a problem in the past with refrigerant leaking, was supposed to be fixed"
hot air supposed to be comming out of the condenser while in operation if not the compressor may not be running check the capacitor for swelling or a leakage
Posted on Sep 26, 2009
Tips for a great answer:
Jan 06, 2017 | Heating & Cooling
Dec 11, 2013 | Computers & Internet
Nov 02, 2012 | Refrigerators
May 04, 2011 | Mitsubishi MS09TW Air Conditioner
Dec 26, 2010 | Fujitsu Heating & Cooling
Oct 23, 2010 | Plumbing
Jul 18, 2010 | 2000 Toyota Camry Solara
Jun 20, 2010 | Dometic Rooftop RV Air Conditioner
Nov 08, 2009 | Fujitsu 24C1 Air Conditioner
Aug 17, 2009 | Heating & Cooling
1,285 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: