Question about Goodman Heating & Cooling
Posted by Anonymous on
What refrigerant are you using? with r-22 the high side should be around 230 to 250 psi and suction should be 68 to 70 psi.
Posted on Jul 04, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: have goodman unit, ac unit
You should have liquid line filter/dryer that maybe restricted or there is a restriction in the orfice inside the evap coil normal operating pressures are 68/ 180
Posted on Oct 07, 2008
Hello, if this is a R-22 unit your low side should between 70-75 psig and high side should be between 225-230psig. But keep in mind always measure the superheat if it is a fixed orifice and subcooling if it is a txv unit
Posted on Jun 07, 2011
Tips for a great answer:
May 27, 2015 | Goodman Heating & Cooling
Sep 02, 2014 | Goodman Heating & Cooling
Apr 20, 2014 | Goodman CLQ36AR49 Air Conditioner
Aug 26, 2013 | Goodman CKL36AR36 Air Conditioner
Aug 01, 2011 | Goodman CKL30AR30 Air Conditioner
Jul 17, 2011 | Goodman Heating & Cooling
May 11, 2011 | Goodman Heating & Cooling
Aug 09, 2009 | Goodman CLQ36AR49 Air Conditioner
Oct 07, 2008 | Goodman Heating & Cooling
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: