Question about Heating & Cooling
The ignitor starts and the gas goes on but the blower does not always come on with heat, and it is not because the house is warm enough that the thermostat is higher than the tempature set.
Sometimes the ignitor starts and then goes off and the blower starts with cold air.
What could cause this if the ignitor was replace and the filter was just replaced?
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 25, 2012 | Heating & Cooling
Sep 04, 2012 | Amana ALG443RAW Gas Dryer
Jun 28, 2011 | Amana NGD7200TW Gas Dryer
Jul 11, 2017 | Ruud Heating & Cooling
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution: You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 26, 2010 | Heating & Cooling
Sep 06, 2010 | Dryers
Feb 24, 2010 | Whirlpool GGW9250PL Gas Dryer
Jan 11, 2010 | Bryant Heating & Cooling
Dec 09, 2009 | Estate TGDS740JQ Gas Dryer
Dec 04, 2009 | Heating & Cooling
95 people viewed this question
Usually answered in minutes!