Question about Goodman GMS90703BXA Heater
The red lick is blinking 3 times. The blower fan will not kick on. Can't get furnace to kick on. Just cleaned everything. Been having problems with central air too. Been a build up of ice around the pipes and seems like we have to let it thaw before we can get the system running again.
These are two unrelated problems. The flash code you are getting is an induced draft problem. The pressure switch is not proving airflow. Make sure that the inducer motor (the motor in the middle of the top door) is running when calling for heat. If so, make sure that the flue in not obstructed. Bird nests, rodents, ice, and snow can plug the flue to the point that not enough air is being moved to allow for ignition.
As for the "ice around the pipes" can be a couple of issues. Check to make sure that your filter has been replaced. If the indoor blower cannot move enough air, the coil will freeze. If that is not dirty, then you most likely have a refrigerant leak and need to have it recharged.
Posted on Oct 07, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 05, 2015 | Heating & Cooling
Feb 03, 2015 | Heating & Cooling
Oct 12, 2011 | Goodman GMS90703BXA Heater
Sep 06, 2011 | Goodman Heating & Cooling
Feb 23, 2011 | Intertherm Heating & Cooling
Jan 16, 2011 | Goodman GDS80904BNA Open Flame Heater
Jan 14, 2011 | Goodman GMS90703BXA Heater
Dec 29, 2009 | Heating & Cooling
Feb 06, 2009 | Carrier Heating & Cooling
Feb 01, 2009 | Goodman GMS90703BXA Heater
168 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: