Question about Heating & Cooling
Any recommended remote as alternative to tadiran tac490? M
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I'm not sure exactly what unit you have and what controls you have installed on the unit. But....there usually is a flash code schematic on the unit. Usually on the inside of the blower compartment cover. This should tell you what is wrong with the unit. It could have a low voltage short somewhere and is loosing the call for cool. So the answer can be a possible yes to your question but without knowing the flash code, it's hard to tell from my point of view. You might end up calling a service professional out to check it.
Posted on Mar 30, 2009
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
If anything, it appears undercharged. Purging is not recommended. @90 degrees the high side corresponding pressure is 168.4 and Low side coresponding numbers re70psi/68degrees. With all due respect to the tech I think . If your room temp is 80, the corresponding high aide pressure is 143.6 , Low side 85 psi Yup, undercharged. Now do me a favor and don't start any "but he said" wars going. If anything, Just call him back and tell him something is still not right. Ask him to bring you a pocket rergerence for temp/pressure relationships. The numbers I gave you are for R-22 which is commonly used in residential applications. Well, good luck and keep your cool. IDon't purge. R-22 is very expensive asis everything else. You may want to dispute anny additional service call charges. Good Luck
Posted on Aug 22, 2009
Here is where you can find all the info you will ever need about Mitsubishi Air Conditioning units...
Check out this tip that I wrote about that...
Mitsubishi Air Conditioner Troubleshooting and Repair
Posted on Aug 20, 2010
Tips for a great answer:
May 29, 2016 | Mitsubishi Heating & Cooling
Apr 25, 2016 | LG Heating & Cooling
Dec 31, 2015 | Heating & Cooling
Apr 30, 2017 | Mitsubishi 18000 Btu Mr.slim Ductless Mini...
Jun 11, 2017 | Heating & Cooling
Dec 26, 2010 | Mitsubishi Heating & Cooling
Mar 30, 2009 | Carrier 38CKC042 Air Conditioner
Dec 26, 2007 | Heating & Cooling
Aug 31, 2007 | Mitsubishi MSH09TW Air Conditioner
67 people viewed this question
Usually answered in minutes!