Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: lg split system air conditioner
Try sutting off the power to both units. This may reset the unit. Check out the service manual at LG website www.lgusa.com. Go to their support page and put the model number in. Remove and replace the batteries in the remote. If there is a communication error, the inside unit will display 3 flashes. If all else fails, call LG at 1-800-243-0000. Good Luck!
Posted on Aug 30, 2007
The model number would be on the right hand side of the outdoor unit and same on the indoor unit if it is a midwall split. If it is a flat cassette cieling type you may need to open the grill, which is simply two little levers either side of the grill, and the grill will swing open. Without the model number it is difficult to give accurate info. However, I can offer the following. One, check the condensate drain. You can just blow into the drain pipe from the outside and this sometimes clears clogged mud in the drainpan. Or two, error reading can also come from phase failure (in the case of a three phase unit) or power related problem. This can be solved by switching off the mains and then switching on again to reset. If you have a phase failure you would need an electrician to confirm that the power supply is good. Unless you have a volt meter.
Posted on Mar 04, 2009
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
Tips for a great answer:
on May 10, 2015 | LG Heating & Cooling
Apr 14, 2016 | LG Heating & Cooling
Sep 01, 2015 | LG Heating & Cooling
Dec 24, 2014 | LG Heating & Cooling
Feb 11, 2011 | LG Heating & Cooling
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Nov 29, 2009 | LG Heating & Cooling
Oct 18, 2017 | Heating & Cooling
80 people viewed this question
Usually answered in minutes!