Question about Heating & Cooling
Two things are the most likely culprit. First check ytour inside coil with the unit running for 10 minutes or more and see if the coil is sweating there should be water running off of it. Also after one hour is there ice forming on it. These problems are lack of air flow which is caused by restricted air flow caused by a dirty filter dirty coil (which you have already taken care of) or your blower motor may not be kicking into high speed. Your motor will start and then after it gets to a certain speed it switches to a high speed. After running only 15 minutes if your blower motor is hot to the touch. Be careful some will cook an egg. If it is hot not just warm it is bad and needs to be replaced. Also if the fan is not running properly you can not get reliable readings with your gauges when adding freon. So if this is the problem then you may have to have the units freon cked again. If the line is not sweating at the outside unit where it goes into the unit the freon pressure is not right. The larger copper line will be cold and sweating the small line will be hot to the touch when the system is balanced and running properly. I hope this helps
Posted on Aug 23, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 28, 2017 | Heating & Cooling
Aug 09, 2017 | Carrier Heating & Cooling
Mar 15, 2017 | Heating & Cooling
Nov 04, 2017 | Heating & Cooling
Sep 22, 2009 | Carrier Heating & Cooling
Jun 28, 2009 | Dometic Rooftop RV Air Conditioner
May 09, 2009 | Carrier Heating & Cooling
Mar 30, 2009 | Goodman Heating & Cooling
Jan 31, 2009 | Carrier Heating & Cooling
Apr 26, 2008 | Heating & Cooling
71 people viewed this question
Usually answered in minutes!