Question about Heating & Cooling
Take the cover/door off n it should b on the back
Posted on Nov 09, 2012
Testimonial: "Hi Al The unit do not have the cover any more. There are 1 cap missing need to know the size and the wiring? 1 cap running to comp are there and fan cap also there. "
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: carrier multi hi wall split a/c
I don't have a diagram, but maybe I can help you. You have 2 compressors, o.k. 2 stage system. A single phase contactor? do you mean a single pole, one side breaks, the other is always hot? Speaking of phases, is this a commercial unit with 3 phase? Also, Each compressor needs a separate contactor to carry the load. What is the question?
Posted on Dec 23, 2007
I assume you know if this is correct voltage and single or 3 phase, and whether it will fit your application or not, how is the duct work going to attach, how many people will be in the conditioned area, what is the building made of, how much insulation is has...
A little more to it than just "turn it on".
If you get the models and serial and can contact the manufacturer or their representative you might get a wire diagram. Most any package unit would do. As long as you keep the original equipment controls. If you "patch" it up it may be hazardous by not having safety's where it was designed for. Or for instance It may have a anti freeze thermostat. By passing this could lead to coil freeze up and compressor damage. Leaving out a pressure switch (if any) may do the same or could become dangerous to people in the event of fan motor failure. A low temperature fan speed switch may not be needed now unless you plan to run the AC in below 55'f.
And a few dozen other factors that might need to be considered.
If you feel confident after this then contact carrier.
Please rate me as high as you can and thanks for using fixya.
Posted on May 19, 2009
Search this web site. It has lots of manuals. It is Carrier site.
Hope this helps. Wiring diagrams are hard to find but I know they are there if you input enough of the right info.
Hope this helps and be patient while you search.
Posted on Nov 22, 2009
see page 2 here...the drawing section with H (hermetic compressor) F (fan) and C (common. -- http://www.docs.hvacpartners.com/idc/groups/public/documents/techlit/38en-1w.pdf
Posted on May 10, 2010
Tips for a great answer:
Aug 24, 2011 | Carrier Heating & Cooling
Jul 17, 2010 | GE 18 Hp Capacitor Start Ac Motor 115...
May 28, 2010 | Proform XP 590S TREADMILL Drive Motor
May 27, 2010 | Carrier 38CKC036 Air Conditioner
Nov 20, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
May 19, 2009 | Carrier Heating & Cooling
May 17, 2009 | Carrier Heating & Cooling
Dec 22, 2007 | Carrier 38CKC036 Air Conditioner
170 people viewed this question
Usually answered in minutes!