Amana Heating & Cooling - Recent Questions, Troubleshooting & Support
I'm not getting any code after installing a control board for my Amana ptac?
Does the power light come on?
If yes, then you can do a reset as below:
There is a master switch on the bottom left of the control board. Slide that to 'off' position.
Then press the hot and cold switch/key together and then slide the master switch back to 'on'.
Please put your response/observation here if that does not work or there is power light as asked on top.
Amana PTH153B50AM PTAC where the heat runs intermittently.
i'm not familiar with your specific unit but ..sounds like an electronic gas value has gone bad or has a bad connection when that happened to my friend it wasn't that expensive to have it fixed .. BYW it acted like this for a while then stopped working completely
Furnace blower won't stop running
Usually when the furnace blower motor runs all the time
The limit switch or rollout switch is usually open or bad.
The furnace board is seeing that one of those switches is open, so it brings the blower on to try to get the heat out of the combustion chamber area, so the switch will close. But if the switch is bad and won’t close, the furnace board will keep the blower running continuously.
Amana Wall unit blows cold air before heating
The cold that you describe may be just unconditioned air? If you are certain you can hear the comp operating for a couple of minutes, and then the heat starts, I would guess it is a reversing valve issue if it's a heat pump and it probably is. Or the control board acting up. I've had a lot of issues with the boards in the Amanda PTAC units. I can't remember how to configure it, but if you Google "Amanda ptac configuration", there is a lot of info online. May try a reset method first. Hope this helps!
Unit will not turn on
To operate the unit without having the remote .. Turn the unit OFF and unplug it for 15 minutes. After the time has elapsed, plug the unit in and turn the ON/OFF Switch to ON. You should now be able to operate the controls on the unit itself. As it should have reverted back to the original factory setup settings.
Hope this helps you and thanks for choosing FixYa.
I have an Amana AP148D, can I run it without an
Self evaporating simply means there is a drain pan with a heater device installed that will evaporate and condensate that drains from the unit into the pan.
You do not need the external drain pan unless the unit makes more water than the drain pan and drain pan heater can handle.
Hello i got a AMANA
I have the Maytag version of this machine and the blinking triangle
light means the water tray is full. The machine won't operate until
that water has been drained -it's the little black tube with the plug
at the bottom behind the machine. Pull the plug, tip it down
(preferably with a shallow pan underneath to catch the water) and drain
as much as you can. Once you've done this, put the plug back in and it
2 problems.. AC Comp cuts out. And Fan will not stop.
Unit#2 -Sounds like the contacts on the master switch are welded closed or the switch is broken, Replacing the switch should fix this unit.
#1 is a little more difficult to diagnose. The compressor is being taken off line by a circuit that protects the compressor from damage either; 1- liquid refrigerant getting back to the compressor which can be caused by something as simple as a clogged return air filter or evaporator coil on a heat pump or 2- overload situation caused by a bad condenser motor or a clogged condenser coil. The first thing you need to do is clean both coils and replace the filter,. Then check to be sure your getting good airflow across both coils. I think it's most likely an airflow issue I hope this resolves the problem GL!
7/9/2021 5:33:18 PM •
on Jul 09, 2021
Not finding what you are looking for?