Question about Kohler 12 kW Emergency Power System - 12RES-L
Is there a fault?? All UL listed generators including Kohler are required to lockout on a fault on shut down. This really sounds like a problem with your 2-wire auto start connection between your automatic transfer switch and genset. RDT model automatic transfer switch it is the 2 middle wires on the green connector and terminals 3&4 in the generator. close to run and open to shut down. Any open at any time will cause the unit to shut down. The 12 will shut down instantly upon an open because your 5 minute cool down is built into the transfer switch.
Posted on Jul 04, 2011
Tips for a great answer:
Jul 17, 2012 | Cars & Trucks
Jul 24, 2011 | 2004 Kia Sorento
Jun 13, 2011 | Kohler Electrical Supplies
Jun 12, 2011 | Electrical Supplies
Apr 14, 2011 | Garden
May 10, 2010 | Watts Onan Portable Generator - 4000 ,...
Feb 05, 2010 | 2003 Chevrolet Silverado 2500HD
Jan 19, 2008 | Heating & Cooling
1,222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: