I have a goodman gsc13 ac unit about 4 year old. When the temp gets around 90 or above outside the fan on the unit starts but the compressor does not. I had service check it out but that day they were...
It sounds like the unit may be over charged. Make sure the outside coils are clean and you have plenty of airflow coming out of the top of the outside unit. What could be happening is, when the temps get higher outside, so do the pressures in the system. The compressor has a thermal overload protection that will kick the compressor off if it gets to hot, which if the compressor is over charged, it will work twice as hard, over heat and shut off. You would need a technician to come out and get the refrigerant charge back to normal. Another thing that could be happening is a weak or faulty capacitor, which is a small round or oval metal object, found in the electrical compartment on the unit. This are fairly simple to change out if your comfortable with electric. I've also had to put what's called a hard start kit on compressors with the same problem, new and old. The hard start basically gives it that extra boost of power to get it up and going. I would start with the refrigerant charge and go from there. The electrical "humming" sound that you hear unless you turn the breaker to the furnace off, is the contactor on the outside unit having a call for cooling. The 24 volts come from the furnace, to the outside unit, and pulls the contactor in to power the unit with the 220 volts supplied. It is normal and you don't have to worry about that at all. I hope some of this helps and good luck!
Jul 05, 2011 |
Heating & Cooling