Question about Heating & Cooling
I can't find that model number on the Amtrol site, please check it.
Is this a water storage tank? With an air charge?
Remove the dust cap on the charging valve on top, Schrader valve, like a car tire.
Use a small tool to slightly depress the pin in the middle.
If water comes out, the tank should be replaced but adding air will help for a while.
If air comes out, you can pressurize.
Determine the pump turn on and turn off pressures using a good pressure gauge.
Turn on may be 30 psi, turn off should be around 50 psi, TYPICALLY.
Switch the pump off.
Open a valve and drain all pressure from the water system.
Get a tire pump and pump up the tank pressure through the top valve to 2 psi lower than the pressure that the pump turned on above. If the pump turned on at 30 psi, pump up to 28 psi.
Put system back in service.
Posted on Feb 13, 2011
Tips for a great answer:
Mar 01, 2015 | Goulds Pumps Goulds J5S Jet Pump Shallow...
Aug 22, 2014 | Amtrol WX-302 WX-302 150S1, 86 Gal...
Feb 12, 2013 | Heating & Cooling
Aug 07, 2011 | Amtrol ST-12-C THERM-X-TROL ASME Expansion...
Jun 06, 2011 | Ruud Heating & Cooling
Mar 28, 2010 | Amtrol ST-12-C THERM-X-TROL ASME Expansion...
Jan 04, 2010 | Amtrol ST-5-C THERM-X-TROL ASME Expansion...
Oct 10, 2009 | Plumbing
May 18, 2009 | Amtrol Water Heaters
May 12, 2007 | Kenmore Elite 21086
Usually answered in minutes!
Step 2: Please assign your manual to a product: