Question about Goodman Heating & Cooling
With furnace OFF ,Disconnect the top of the hose that leads to the
Bottom of Daft inducer Box, Now blow into it water will come out
of the drain hoses "condensation " this will shut the unit down if not drained. There must be a Trap on the side of the Furnace with water in it , to have positive presure to suck out condensation. This will fix problem. some installers forget to install this Trap that comes with Unit.....!!!! A little item
that will shut the whole system DOWN. :o)
Posted on Feb 04, 2013
ok this is going to sound funny but it seems as though the polarity is reversed going into your furnance. to correct this proiblem you first need to unplug the unit and where the cord goes into the furnance at that connection disconnect the two wires. Once theses are disconnected switch the wires .All you are doing is reversing the way the electricity flows into the circut board. I would wager that is the problem
Posted on Apr 16, 2009
Using a voltage meter check and see if you have 120 volts at the motor... if so then the motor is bad....
If there is no voltage to the motor then the board is bad....
Replace the motor or board as needed...
Posted on Nov 13, 2010
Tips for a great answer:
Feb 27, 2014 | Goodman Manufacturing Goodman...
Oct 07, 2013 | Goodman Manufacturing Goodman R410A 13...
Oct 05, 2011 | Goodman GMS90703BXA Heater
Dec 02, 2009 | Goodman GMS90703BXA Heater
Jul 14, 2009 | Goodman GMS90703BXA Heater
Jan 20, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 10, 2009 | Goodman GMS90703BXA Heater
404 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: