Question about Ultra (ULT31502) UPS System
Place your two new type CB1270 batteries on their sides, one on top of the other in front of you with the battery connectors closest to you and with the battery connectors to your left. Connect the short (2 inch) jumper cable between the two center battery posts (1 red/1 black). Slide the battery stack into the chassis with the battery posts to your left as you face the front of the UPS and be careful that the battery posts do not touch the metal chassis. When the batteries have been slid completely into the chassis, connect the heavy red wire from the circuit board to the red battery connector at the bottom of the battery stack and the heavy black wire from the circuit board to the top black battery connector. If you have doubts about your wiring, use a DC voltmeter set to the 50v range and touch the red probe to the red battery post at the bottom of the battery stack while touching the black probe to the black battery post at the top of the stack. The reading on your meter should be somewhere between +24 and +26v depending on the charge level of your batteries.
Posted on May 01, 2011
Tips for a great answer:
Dec 22, 2015 | Powercom BNT-1000AP (dspcmbnt1000ap) UPS...
Feb 21, 2011 | Powercom BNT-1000AP (dspcmbnt1000ap) UPS...
Aug 06, 2010 | Pride Go-Go Ultra X 3-Wheel Travel Scooter
Mar 15, 2010 | Jet 3 Ultra Power Chair
Jun 29, 2009 | D-Link DWL-1000AP and DWL-120 Wireless USB...
Mar 31, 2009 | Powercom KIN-1000AP (kin1000aprm) UPS...
Nov 05, 2007 | Biostar M7NCD ULTRA Motherboard
Jun 22, 2020 | The Computers & Internet
2,269 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: