Question about Nor-Lake Norlake Refrigeration 4' x 6' Kold Locker Walk-In Cooler - 6' 7'' High w/Floor
I’m happy to assist further over the phone at https://www.6ya.com/expert/david_dc2f9e0a44104720
Posted on Oct 18, 2017
The evaporator drains into pan with a coil from the discharge line. The design is intented to sub-cool the liquid refrigertant as well as evaporate the condensation from the coil. Unfortunately the engineer started as career a shipping clerk and never received any further training. There isn't enough heat or running time to evaporate the condensation from the coil.
The solution is fairly simple
A plastic tube drains water out of the evaporator in the pan. You can extend the tube and add a defrost pan handled by your refrigeration wholesaler. Wire it so it is on whenever there is power to the unit. This should get rid of the excess water. These pans are also used on some self contained coolers and freezers. They come in either 120 volts or 220 volts. [email protected]
Posted on Jul 27, 2009
I have a generic wiring diagram that I use on all my installs that works very well. It is basically the same for most all commercial walk in freezers. Send me a email address and I'll scan and forward what I have.
Posted on Oct 16, 2010
Tips for a great answer:
Jul 04, 2017 | Heating & Cooling
Apr 27, 2014 | Nor-Lake Freezer Norlake Refrigeration 6'...
Apr 22, 2014 | Freezers
Sep 12, 2011 | Nor-Lake Freezer Norlake Refrigeration 6'...
Oct 10, 2010 | Nor-Lake Freezers
Jan 20, 2010 | Master Bilt Commercial Freezer 860808
Jul 12, 2009 | Nor-Lake Norlake Refrigeration 4' x 6'...
May 24, 2009 | Nor-Lake Freezer Walk In Freezer 6ft x...
Dec 24, 2008 | Nor-Lake Freezer Norlake Refrigeration 6'...
May 07, 2008 | Nor-Lake Norlake Refrigeration 4' x 6'...
222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: