Question about Heating & Cooling
There can be a couple of things that could be happening...
The first and easiest thing is to check the air filter. Make sure that it is clean... clean it or replace it. Next check the air vents to make sure that they are open and giving you good air flow...
Also check to make sure that you are not icing up on the indoor coil... ice will tell you that you are low on refrigerant. You also could be low and not be icing over, but you would need to have gauges on the unit to check that.
Finally check and clean the outdoor coil...this also can give you problems if the heat is not being removed from the outdoor unit efficiently...
You may also have a unit that is sized in such a way that it hits the balance point at about 85...that means that your heat gain is equal to the capacity of the unit...I often try to size them for about that here in Northern PA. because wqhen seldom get hotter then that and the unit then is much more effective at removeing humidity at lower temperatures...
You can also check out the tips that I have wrote about Air conditioning trouble shooting and maintenance...
Here is one about cleaning the condenser coil and at the bottom of that one are links to others..
Condenser Coil Cleaning Condenser Coil Cleaner
Posted on Jun 25, 2010
Tips for a great answer:
Nov 16, 2014 | Heating & Cooling
Sep 10, 2014 | Heating & Cooling
Aug 04, 2014 | Panasonic 36PEF1U6 31,200 BTU Single Zone...
May 26, 2014 | Haier Heating & Cooling
May 11, 2011 | Quasar Heating & Cooling
Jun 25, 2009 | Heating & Cooling
Jun 10, 2009 | Heating & Cooling
May 04, 2009 | Heating & Cooling
Jan 15, 2021 | Heating & Cooling
546 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: