Question about Heating & Cooling
Posted by Anonymous on
It sounds like your inverter is at fault. You will need an inverter tester ( most good service techs will have one ) to prove that the output to the compressor is correct. If the inverter is okay then it will be the compressor at fault with a location error or it is simply seized. A common fault that caused this was the eev remained closed (coil failure ) and caused the compressor to over heat.
Posted on Jul 15, 2010
Tips for a great answer:
Apr 16, 2018 | Fujitsu Heating & Cooling
Nov 15, 2016 | Fujitsu Heating & Cooling
Jul 10, 2015 | Fujitsu ASU9RLS2 Single Zone Wall Ductless...
Feb 19, 2015 | Fujitsu Heating & Cooling
Dec 17, 2014 | Fujitsu Heating & Cooling
Feb 05, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Dec 27, 2010 | Fujitsu 24C1 Air Conditioner
Sep 18, 2017 | Fujitsu 18C1 Air Conditioner
May 16, 2009 | Fujitsu 24R1 Air Conditioner
Jan 05, 2009 | Fujitsu 18C1 Air Conditioner
1,166 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: