Question about LG Heating & Cooling
First off, check power:disconnect box outside may have fuses,then check power at fuse box.If you have power(220 volts) then check for 24 volts at T-stat line.Also, make sure T-stat is set to A.C.With power on go outside and listen to condenser unit.If fan is rotating listen for humming .If it is not running, it could be a bad contactor or a bad or capacitor .If it is running check after 5+ minutes if warm air is coming out of the outside unit.Also, wash the condenser unit:start by spraying the hose about 45 degrees downward ,going side to side,and down on all sides.Do Not use High pressure hoses,it will bend coil fins.After it runs for about an hour,or so, go out and see if low pressure line(big one) is sweating and cool, and high pressure line (small line) is warm.
Posted on Feb 23, 2010
Tips for a great answer:
Aug 13, 2014 | Amana PTH123B25AJ Heat Pump Air...
Sep 07, 2011 | Heating & Cooling
Sep 03, 2011 | Ruud Heating & Cooling
May 22, 2011 | Heating & Cooling
Jul 04, 2009 | Heating & Cooling
May 31, 2009 | Ruud UBHC Air Conditioner
Oct 27, 2007 | Ruud UBHC Air Conditioner
177 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: