Question about Tylo TS30-01 Control Panel
I am Electrical Engineer on accomodation vessel. We have two saunas on board the vessel and have a requirement to renew /Replace one of our Tylo controllers.
The old model number is ET 32-12.
One of my colleauges had already ordered a replacement for this, which was a TS 30-12 Manuf no 352253155
This was not suitable for our installation as it was a purely mechanical timer switching 3 phases with a temperature controller with its own short capillary wire for the stat
Approximately 18 inches long.
This is not suitable because the controllers for both our saunas are situated around 4 to 5 metres form the sauna itself .
What we require is a controller incorporating its own three phase contactor that will tie in to field wiring for the high temeperature cut out thermostat.
Which is exactly what the original controller did, it had a pcb card that when adjusted the temperature controller at the unit itself then would send a signal to a 24 volt relay that would switch the 220 volt control circuit to energise the external three phase 220 voil contactor to supply volatge to the heating elements.
W have another sauna that actually has a TS 30- 012 controller that incorporates all the things the old controller had Manuf number 91304 200 .
This is exactly what we would like to order but cant get part number with one with pcb
Can you please advise as to what we can order that would suit this criteria?
You need a Tylo cc50 controller and the R30 relay box then you can run it as long as the current capacity of your cable
Andrew UK Saunas Ltd
Posted on Aug 09, 2010
Hi Andy, I am Kelly and wish to at least make an attempt to help you out. I have done quite a bit of research and like you have come up with little nothing positive.
You may have to buy your own 3 phase 24DC controlled contactor and control that with a yet another relay.
At this point you may want to call Tylo direct or email them and explain your needs to see if they can help you.
Page 8 of their installtion manual shows several 3 Phase connections
Tylo contct info:
TYLö AB, Svarvaregatan 6, S-30250 Halmstad, Sweden.
Tel +46 35 10 00 80, Fax +46 35 102580. E-mail: [email protected] Internet: www.tylo.se
Here is the controller you may need with a 5 meter capillary tube. it does not say if it is 3 Phase and it is mecanical.
Seriously I would contact Typo directly via the contact info above and solve your problem quickly.
The link.... for the TS-30-012
I do wish you the best.
Posted on Jan 26, 2010
Testimonial: "Thanks for all the info and shall contact Tylo direct Andy"
Tips for a great answer:
Aug 23, 2014 | Tylo Deluxe 11kW Sauna Heater, w/ TS30-01...
Jan 15, 2013 | Tylo Super Sport 7 Sauna Heater
Nov 23, 2010 | Tylo SUPER SPORT-U8 Sauna Heater 8 kW
Jan 23, 2010 | Tylo SPORT-U2 Sauna Heater 2 kW
730 people viewed this question
Usually answered in minutes!