Question about Heating & Cooling
Can you tell me where I can get the wiring diagram/schematic for my Ruud heat pump, model number UHQA1210BNS. Had a water problem that caused the diagram on the inside panel for the electrical connections to become difficult to read. Tried gently cleaning diagram to remove the rust/dirt. It helped a little until part of the paper started to come off.
My immediate conern is to learn what the orange wire, coming out of the Ruud air handler (the unit inside the house), connects to. Either to the thermostat and/or the control cable going to the outside unit.
This is a 2nd posting. My 1st posting was a little unclear after I re-read it.
Thanks in advance,
We are trying to install a goodman heat pump with a rheem air handler, the orange wire is hook up and the unit is still staying in the heat mood. does anyone have a wiring diagram for the air handler, their is some white wires in the air handler one with a purple strip and one with a black strip we need help
Posted on Aug 19, 2009
Wiring diagram for heat strips ruud??
Posted on Jul 14, 2011
The orange wire coming out of the outside unit is for the reversing valve( controls the heat and cool mode of the ac) If its unhooked, it will be either in the ac mode all the time or the heating mode all the time depending on the style of the reversing valve. The orange wire goes to the (O terminal) inside the outside unit.
There is also another orange wire that goes from the air handler to the thermostat. One orange for the thermostat, and another to the condenser( out side unit)
Posted on Jan 26, 2008
What does the the purple wire on a Rudd unit connect to
Posted on Apr 19, 2019
I'm a Certified HVAC Technician and have been working in this industry since 1996. I simply went too www.google.com and typed in RUUD HEAT PUMP WIRING DIAGRAM, and found the following website URL where you can view and download and print your own PDF copy:
But, for your information, in MOST cases, standard COLOR Coded WIRING for HEAT PUMP applications shows the ORANGE wire gets landed onto the "O" Terminal on the Heat Pump Thermostat, at the AIR HANDLER both ORANGE WIRES simply get twisted together and capped off with a WIRE NUT, and the ORANGE WIRE on the OUTDOOR UNIT also gets twisted together with the ORANGE WIRE coming down from the AIR HANDLER UNIT and capped off with a WIRE NUT. Therefore, O = Orange Wire = Reversing Valve. Good Luck
Posted on Sep 20, 2012
If the Line and Neutral are swapped in a Aircon Wiring what happens when it is run ?
Posted on May 05, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 22, 2014 | Rheem 3 Ton Air Handler - RHLLHM3617JA
Oct 07, 2011 | Ruud UBHC Air Conditioner
Jul 10, 2011 | Heating & Cooling
Mar 10, 2011 | Ruud Heating & Cooling
Apr 07, 2009 | Ruud UBHC Air Conditioner
Feb 03, 2008 | Ruud Handler Air Conditioner
Jan 04, 2008 | Heating & Cooling
Nov 24, 2007 | Ruud UBHC Air Conditioner
Sep 02, 2007 | Ruud UBHC Air Conditioner
5,837 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: