Question about Fujitsu Heating & Cooling
SOURCE: Fujitsu Heat Pump - problems
I had the same problem. The heater did not work in heating mode. However it was OK in air-conditioning mode. The operation light and the timer light blink twice and then the operation light blinks for 5 times followed by few seconds non blinking, then the cycle repeats again. I have read on the internet that you better unplug the power cord and then plug it again so that the heater re-sets itself. My only problem was that my heater is directly plugged to the power with no visible plug. So I went to the main distribution board and put off the power for about 20 seconds for the whole home. HOORAY!! The heater worked after that.
Posted on Aug 08, 2008
same problem as others 3 blinking green lights then orangey colors then 3 red blinking lights afterwards shuts down fan runs for about 2 mins solution check your door cover for warpage or deformed just a bit under set screw there is a push in switch try and push it in with q tip while holding turn on tv if it works then that door is deformed and defective change it
thanks for solving my issue tv works again very helpfull thanks
Posted on Jan 07, 2009
trying to get the compressor to operate. it could be a bad capacitor and the compressore wont start or maybe the compressor is burned up
Posted on Dec 15, 2009
Testimonial: "Thanks for the advice. It turned out that we had a blackout after the AC had started playing up. The blackout seems to have sorted out the problem.Thx"
SOURCE: I have a fujitsu AOTR30LCT,
Error c0de-3.Return air thermistor short circuit.
This sensor when it's defective, will not command for compressor for working.
Replace it.(Room air sensor). Helpful?
Posted on Jan 24, 2011
Testimonial: "Thanks that worked called the fujitsu people and they replaced the faulty sensor"
Tips for a great answer:
Nov 15, 2016 | Fujitsu Heating & Cooling
Jul 11, 2015 | Heating & Cooling
Mar 26, 2015 | Fujitsu 15RLS - ASU15RLS2 - AOU15RLS2 -...
Feb 10, 2015 | Fujitsu Heating & Cooling
Dec 13, 2012 | Heating & Cooling
Mar 21, 2009 | Fujitsu Heating & Cooling
Mar 14, 2009 | Friedrich MR18Y3F Split System Air...
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
Usually answered in minutes!