Question about Dayton Heating & Cooling
Yes, the flame sensor is part of the intermittent pilot assembly. Check the following: make sure all grounding wires are secure and no corrosion is built up on them. Clean or replace the pilot assembly, also clean out the orifice with a very small drill. Make sure the sensor is in the flame and make sure the pilot tube is not leaking gas reducing the gas pressure at the pilot.
If it continues, you will have to replace the ignition control.
Posted on Nov 26, 2007
Does the main blower fan kick on? Also, if the heater is vented outside via a flue pipe, there may be a small (about 3 or 4 inches in diameter) vent fan that kicks on to ensure the exhaust fumes are evacuated through the flue pipe. If there's a problem with that fan, the burner won't light either.
Posted on Nov 20, 2008
Contact Dayton on the internet for this problem. The diagram should be available on their site. Or they will give you a number for customer care. They can give you step-by-step instructions. I am a technician and this is what I would do as their are millions of wiring diagrams. Many are noy up to date.
Posted on Dec 07, 2008
Tips for a great answer:
Jan 05, 2016 | Dryers
Feb 12, 2015 | Dayton Heating & Cooling
Aug 18, 2011 | Dayton (3E132) InfraRed Heater
Feb 06, 2011 | Dayton (3E132) InfraRed Heater
Dec 12, 2009 | Dayton Heating & Cooling
Dec 11, 2009 | Dayton Gas Furnace Heater
Apr 07, 2009 | Dayton (4LX41) Heater
Dec 07, 2008 | Dayton (3E379) Heater
Jan 04, 2021 | Dayton Heating & Cooling
12 people viewed this question
Usually answered in minutes!