Question about Kohler Electrical Supplies
Locked Rotor is reported as an overcrank fault "OC".
You first need to verify the engine fails to crank, which is likely a starter motor or start circuit failure.
If the engine cranks three separate times and then the OC fault occurs, it simply means the engine did not run... more likely a fuel issue.
But either can be caused by numerous reasons.
Posted on Apr 25, 2020
OC stands for Over Crank. How long does it take before the genset starts?
Posted on May 07, 2009
Check battery volatge while you are cranking engine if voltage drops below 9 vdc you have a bad battery. If it doesn't you probable have a bad starting solenoid or a bad ground at the starting solenoid.
Posted on Nov 18, 2009
Is the outside air temp cold. These generators will backfire if it is real cold and if the propane pressure is low. It is suppose to be 11 to 12 inches of water colume at the generator fuel input. drygwals
Posted on Feb 20, 2010
Tips for a great answer:
Jan 21, 2018 | Kohler Electrical Supplies
May 19, 2015 | Kohler 20resa 20kw Home Emergency Backup...
Feb 08, 2013 | Kohler 30 KW LP/Propane Industrial...
Oct 25, 2012 | Kohler 17RESL 17 kW Generator with 200 Amp...
Jul 27, 2012 | Kohler 14resa 14kw Home Emergency Backup...
Aug 09, 2011 | Kohler 12 kW Emergency Power System -...
Dec 02, 2010 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Apr 13, 2018 | Kohler Electrical Supplies
52 people viewed this question
Usually answered in minutes!