Question about Bryant Heating & Cooling
Your outdoor condenser is in heat mode. Check the wires on the thermostat. Sounds like a small wiring problem and nothing else. Good luck. Please keep me posted as to you progress.
Posted on Apr 27, 2009
Refrigerants are regulated by the EPA. In order to purchase it, you need an EPA License. If you are low on refrigerant, the leak needs to be found and repaired. This requires special tools.
Additionally, with the information given, it could be an electrical problem. Is the outside fan running, is the compressor running? Your best bet is to call a professional.
Posted on Jul 22, 2010
SOURCE: Have a Bryant 340MAV condensing
Just curious, have you changed your filter out recently? This blog talks about a problem similar to yours and the tech changed out the filter and tapped a screwdriver between the terminals of the limit switch:
If tapping on the limit switch doesn't help, it may have to be replaced.
Here is Bryant's support page:
Good luck, and hope this helps.
Posted on Sep 26, 2010
SOURCE: I am trouble shooting a
if you are using honeywell vision pro 8000 t-stat you need an outdoor sensor program on t-stat would have to look up
I’m happy to help further over the phone at https://www.6ya.com/expert/vincent_f7b7c5f4dedd2565
Posted on Feb 19, 2013
SOURCE: Bryant FA4ANF04200 Operation is intermittent. Some of the time it will go on when set to heat or cool. Other times, it will not turn on. Replaced thermostat. Problem continues. Sounds like defecti
Is this a heatpump system or a gas furnace /a/c system,you have a 3 1/2 ton a/c unit,if it is over 5 yrs old it could be a board problem,look for any spliced wiring where they used little wire nuts to join wires,these can make bad connections,?does the blower turn on,is the outside unit running but no airflow,if you have a gas furnace it may have a window,a little clear lens to look in at the furnace control board,it will blink a failure code if there is a problem,need more info :)
Posted on Mar 09, 2013
Tips for a great answer:
Usually answered in minutes!