Question about Electrical Supplies
We hold parts for your Generator and have a whole Help Center dedicated to helping people fix their Portable Generators. If the answer is not there, we have Generator Engineers who can help. Check it out on our site. https://www.generatorguru.com/
Parts Spares for Generators and Small Engine Machinery
Posted on Aug 19, 2019
my name is scott i work on generators,i realy need more info so ill give u some basics
................1] need to check your brushes u can get to this on the back side of the motor,by tacking out the 4 bolts or depending on the cover a 1"x3" plate
................2]if that is good then i would test out the field or armature
p.s. all of this is done on the motor not the engine, also u may also want to talk to tech support at PRAMAC,this is the suplier for coleman/powermate
Posted on Mar 04, 2009
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
I take it you have RV plugged into generator. Hopefully direct with no extension cords. Are you using a 30 to 15 amp adapter to plug into generator? What is the rating of the breaker on the generator that keeps tripping, suspect it's only 15 amp?
Posted on Jul 20, 2009
There is no problem to use it if the load to be transferred is under 7500 W.
Even a load of 8000 W may be handled for a short time, but if the protection of the switch is adjusted at 7500 W (the respective current), it may drop after some time.
Posted on Aug 07, 2010
Suggest you go to Amazon.com and do a search for the Generac Guardian. When you find it, look in the product details and you will see Product Manual (PDF) under the Product Details. No Battery Charge DC output. 1. Battery posts are corroded. 1. Clean battery posts. 2. Battery cable is bad. 2. Replace cable. 3. Battery is defective. 3. Check battery condition; replace if defective.
it has a troubleshooting guide located on page 19.
4. Receptacle is bad. 4. Contact Authorized Service Facility.
Hope this helps!
No Battery Charge DC output.
1. Battery posts are corroded. 1. Clean battery posts.
2. Battery cable is bad. 2. Replace cable.
3. Battery is defective. 3. Check battery condition; replace if
Posted on Jun 02, 2011
Tips for a great answer:
Sep 09, 2017 | Electric Electrical Supplies
Oct 06, 2016 | Powermate 8750 Watt Portable Generator...
Dec 25, 2014 | Honda Black Max 7000 / 8750 Watt Portable...
May 19, 2013 | Briggs & Stratton Power Products 5,550...
Oct 28, 2012 | Coleman Powermate 7,000 Watt 13 Hp...
Jul 27, 2012 | Electrical Supplies
Jul 28, 2011 | Coleman Powermate 7,000 Watt 13 Hp...
Dec 10, 2009 | Coleman Powermate 7,000 Watt 13 Hp...
140 people viewed this question
Usually answered in minutes!