Question about DeLonghi CF210 Portable Air Conditioner
I have a PAC 03 U model that functioned well until this summer. Now it's leaking buckets. Sometimes the water goes into the reservoir but most of the time it spills all over the hardwood floor. The filters have been cleaned and there doesn't appear to be any obstructions in the intakes. I'm getting weary 'babysitting' the airconditioner! Any solutions??? HELP.
If you have cleaned the air filters then that is the first step. Next you want to check the condenser coil. That is the coil that is outside. If it is dirty you will have a low charge situation which could cause lots of condensation. Also if the condenser coil on the outside is clean and you are getting lots of water than you my have low charge of refridgerant. If that is the case you will need a professional to come and charge the unit and find the leak. Did you check to see that the unit is level. Because is should drain to the outside. The unit should be installed in a way that the water drains to the outside.
Posted on Aug 23, 2009
Tips for a great answer:
Jan 21, 2018 | Samsung Washing Machines
on May 18, 2010 | Dehumidifiers
Aug 13, 2015 | Water Water Heaters
Jul 07, 2014 | Comfort-Aire PAC-121 Air Conditioner
Jul 22, 2011 | Danby Portable Air Conditioner
Feb 15, 2011 | 1999 Ford Windstar
Oct 22, 2010 | Computers & Internet
Dec 02, 2009 | 2000 Porsche Boxster
Aug 19, 2009 | Heating & Cooling
502 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: