Question about Electrical Supplies
check ot see if its on a shunt trip system. what it means is that in order to reset the breaker you have to see what made it trip. Look for a 115 volt breaker that is tripped in the panel that serves tha line. good luck.
Posted on Jan 25, 2009
SOURCE: gfci breaker for spa
gfci's are designed to trip if they receive voltage on there ground/neutral side, therefore my vote is for Smithbrother I would say there is probably a partial short somewhere in you system.
Posted on Mar 24, 2009
You're unit is a 31/2 ton according to the numbers.Normally, breakers will only be in a half way posistion when tripped. Yes, under most conditions, the fuse will blow before the breaker trips. I have seen this many times, the breaker may be weak, burned, loose wires and so tighten wires, check the condition of the breaker.It sounds like the breaker even though it is 60 amps, is the problem and you should replace it with out hesitating. This will solve you're problem. When you pull the breaker out, look at the metal clips that snap in on the buss bar to see if they have been overheating.And the buss bar its self. You will know. I am sure this will take care of you're problem. Good Luck,
Posted on Dec 07, 2009
Testimonial: "Thank a lot this was very helpful"
Tips for a great answer:
Apr 26, 2018 | Cars & Trucks
Mar 05, 2011 | Siemens Murray 125 Amp Circuit Breaker...
Dec 14, 2010 | Garden
Jul 05, 2010 | KitchenAid Superba Architect KSCS25INSS...
Apr 11, 2010 | Pacific Industrial Federal Pacific 50 Amp...
Nov 24, 2009 | 2003 Ford Explorer
Nov 23, 2009 | Refrigerators
Jan 16, 2009 | Heating & Cooling
Nov 06, 2008 | 2000 Oldsmobile Alero
114 people viewed this question
Usually answered in minutes!