Question about Generac Electrical Supplies
If you have some fundamental electrical training/experience.
Fault is displayed when both zero crosses are missing from the controller's input for 1.5 seconds or more. Could be a faulty excitation winding, zero cross circuit, loose wiring, or field boost hardware problem. Same applies here, v1.12 or later firmware should be installed.
Posted on Jun 02, 2019
Tips for a great answer:
Sep 02, 2018 | Honeywell Heating & Cooling
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Mar 01, 2015 | Generac 13,000 Watt / 13,000 Watt Home...
Feb 20, 2015 | Generac Guardian 8kw Standby Generator
Oct 15, 2014 | Generac Guardian 8kw Standby Generator
Oct 05, 2014 | Generac Guardian 8kw Standby Generator
Aug 17, 2014 | Generac Guardian 8kw Standby Generator
Sep 06, 2013 | Generac Guardian 8kw Standby Generator
Apr 12, 2009 | Guardian Electrical Supplies
186 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: