Question about Honeywell HZ322K TrueZONE Kit with DATS, Transformer and HZ322 Panel
Have 27 volts ac at board input. Have 27 volts at zone 2 and damper opens What is the problem at zone 1?
SOURCE: Honeywell TZ-4 Misbehaving
there is a "zone a lone" switch on the upper right side of the panel. Make sure it is in the "occupied" position. I believe that is up. If that doesn't work reply back.
Posted on Sep 18, 2008
There is a way to restore the Factory Defaults via the Advanced Configuration Mode. Be careful, this will require thorough knowledge of you system to reconfigure based on your particular system. Here is a link to the manual to assist you with the Advanced Configuration Mode.
Specifically, pages 6 & 7. Visit this link:
Posted on Feb 14, 2010
Hello,Message AC means that there is no 24volt power to the thermostat from the unit/s it controls.Please check all switches & curcit breakers to the unit/s as there is no low voltage power to the thremostat from the transformer in the unit/s.Maybe got turned off by mistake.
Posted on Nov 01, 2010
Be sure all zones are calling for cooling. Press the purge override and verify air flow on all zones. If one is still not working verify the board is sending voltage to that damper. A meter is a huge help but if all lights are on chances are the damper is stuck. You should be able to free it up but it will just happen again. Either replace damper motor, replace damper or if you can figure out if it is a "spring open" damper, get it open and unhook the wire to that zone. This will keep it open at all times because it can not "power close". Provided that zone CAN stay open all the time. Keep me posted!!
If you need further help, reach me via phone at https://www.6ya.com/expert/thomas_092728000e6acb79
Posted on May 25, 2018
Tips for a great answer:
Apr 29, 2018 | Thermostats Heating & Cooling
Sep 29, 2015 | Cars & Trucks
Nov 17, 2014 | Heating & Cooling
Aug 19, 2014 | Honeywell HZ322K TrueZONE Kit with DATS,...
Jun 12, 2014 | Honeywell Truezone HZ311K Zone Control...
May 31, 2014 | Honeywell Truezone HZ432 Zone Control...
Feb 09, 2011 | Amana PTH123B25AJ Heat Pump Air...
Feb 14, 2010 | Honeywell Heating & Cooling
May 28, 2008 | Honeywell Heating & Cooling
472 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: