Question about Amana Heating & Cooling
Unit#2 -Sounds like the contacts on the master switch are welded closed or the switch is broken, Replacing the switch should fix this unit.
#1 is a little more difficult to diagnose. The compressor is being taken off line by a circuit that protects the compressor from damage either; 1- liquid refrigerant getting back to the compressor which can be caused by something as simple as a clogged return air filter or evaporator coil on a heat pump or 2- overload situation caused by a bad condenser motor or a clogged condenser coil. The first thing you need to do is clean both coils and replace the filter,. Then check to be sure your getting good airflow across both coils. I think it's most likely an airflow issue I hope this resolves the problem GL!
Posted on Jun 12, 2008
Tips for a great answer:
Aug 21, 2015 | Amana Heating & Cooling
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Jun 19, 2010 | Amana PTH093B35AM Thru-Wall/Window Air...
Jan 28, 2010 | Heating & Cooling
Nov 16, 2008 | Amana Heating & Cooling
Jun 11, 2008 | Amana PTH123B25AJ Heat Pump Air...
101 people viewed this question
Usually answered in minutes!