Question about Kohler Electrical Supplies
It worked fine wired as is for 250 hrs. It powered fine this morning then poof! AC sensing loss. Electrician coming later. We'll chk the transfer switch. In Dominica so no utility power yet.
I suspect you will SOMEPLACE find protection fuse(s) for the sense lines from the utility. That is the first place to check.
Posted on Mar 24, 2010
If you are using a Manual transfer switch, then you should manually operate the system. Why don't you use the switch it came with? Why would you use a 200a manual transfer switch on a 17kw generator? The idea is to move your critical circuits into the transfer switch panel. Then it would operate in auto.
Posted on Jul 03, 2010
It sounds like the mains sense wire is disconected from the control panel or the run wire is not being cut by the aux contact on the transfer switch.
Is the transfer switch manual or motorised?
Posted on Feb 15, 2011
Tips for a great answer:
Mar 01, 2015 | Generac Electrical Supplies
Jul 19, 2013 | Kohler Electrical Supplies
Jan 04, 2013 | 1995 Pontiac Firebird
Feb 15, 2011 | Briggs Stratton 7,000 Watt Automatic Home...
Mar 22, 2010 | Generac Guardian 100 Amp Transfer Switch...
Nov 01, 2009 | Guardian Electrical Supplies
Oct 02, 2009 | 1998 Ford F150 Regular Cab
Jul 31, 2009 | 1986 Chevrolet Cavalier 2 Door
May 18, 2009 | 1999 Oldsmobile Alero
May 03, 2009 | Ford F-250 Super Duty Cars & Trucks
Apr 13, 2018 | Kohler Electrical Supplies
883 people viewed this question
Usually answered in minutes!