Question about Pramac Electrical Supplies
PRAMAC GSW 665 > Generators
Start looking at your safety circuits.
1. High water temp
2. Low Oil
3. Low water etc...
From the manual these are the protection circuits.
• Engine protection: low oil pressure, high engine temperature.
• Genset protection: under/over voltage, overload, battery charger failure, battery voltage out of limits,
under/over frequency, start failure.
• Circuit breaker protection: IV poles.
• Differential protection.
Any one of them will trip the fuel relay closed. What you may be able to do is disconnect one at a time each protection circuit and see when the fuel relay opens. (Make sure to reconnect each one if it had no effect on the fuel solenoid)
Once you isolate which circuit it is in then you can chase wires or change the bad switch.
Thanks for choosing FixYa.
Posted on Jun 26, 2010
SOURCE: pramac ES7000 genset
Hi, Something is wrong with the govener (stuck or bent). Look to see for obstruction when you crank the throttle. Or maybe a better spring on it.
Posted on Feb 27, 2012
Tips for a great answer:
May 04, 2016 | Pramac Electrical Supplies
Feb 18, 2015 | Pramac 3000 Watt Gas Generator
Dec 13, 2014 | Pramac Electrical Supplies
Sep 01, 2014 | Pramac Electrical Supplies
Aug 21, 2013 | Pramac Electrical Supplies
Mar 16, 2010 | Pramac Electrical Supplies
115 people viewed this question
Usually answered in minutes!