Question about Carrier Heating & Cooling
I replaced the induced draft motor motor will not start with a call for heat check for volage at cm termal on board when i have a call for heat.
On some of those inducer motors there is also a capacitor in the blower compartment on the left side of the burner section. It is possible that if you have 230v coming from the board CM terminals and if the motor is new maybe you have a bad capacitor in the blower section. Follow the wires to the capacitor and check microfarad reading to that capacitor. Caution there maybe 2 in this area but one is for the indoor blower motor and the other will be for the draft motor. The blower capacitor may be somewhere between 10 or 15 mfd but the draft inducer capacitor will be around 3 mfd. hope this helps
Posted on Mar 04, 2016
Tips for a great answer:
on Dec 04, 2009 | Heating & Cooling
Apr 30, 2016 | Carrier Heating & Cooling
Mar 02, 2011 | Heating & Cooling
Mar 12, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 28, 2009 | Heating & Cooling
Nov 03, 2009 | Carrier Heating & Cooling
Apr 03, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
98 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: