Question about Nor-Lake Norlake Refrigeration 4' x 6' Kold Locker Walk-In Cooler - 6' 7'' High w/Floor
13 years old Nor-Lake walk-in cooler$ freezer both have water leaking problem through ceiling panel for quit some time. Both evaporator pan has been replaced but still have same issue. The cooler unit shows rusty water. Any suggestions?
The evaporator drains into pan with a coil from the discharge line. The design is intented to sub-cool the liquid refrigertant as well as evaporate the condensation from the coil. Unfortunately the engineer started as career a shipping clerk and never received any further training. There isn't enough heat or running time to evaporate the condensation from the coil.
The solution is fairly simple
A plastic tube drains water out of the evaporator in the pan. You can extend the tube and add a defrost pan handled by your refrigeration wholesaler. Wire it so it is on whenever there is power to the unit. This should get rid of the excess water. These pans are also used on some self contained coolers and freezers. They come in either 120 volts or 220 volts. [email protected]
Posted on Jul 27, 2009
Tips for a great answer:
Dec 10, 2015 | Refrigerators
Sep 28, 2012 | Westinghouse 5303281154 Fridgedaire/wci...
Jun 11, 2011 | Marvel (6SBARBSG) Wine Cooler
Sep 14, 2009 | Kenmore Refrigerators
Aug 31, 2009 | Kenmore 73502 / 73504 / 73509 Bottom...
Jul 24, 2009 | Nor-Lake Freezer Norlake Refrigeration 8'...
Mar 07, 2009 | Nor-Lake Freezer Norlake Refrigeration 6'...
Jan 06, 2009 | Refrigerators
Feb 25, 2008 | Nor-Lake Norlake Refrigeration 4' x 6'...
Oct 15, 2007 | Nor-Lake Freezer Norlake Refrigeration 6'...
925 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: