Question about Kohler Electrical Supplies
Your gas pressure is too low and you may not have a large enough supply pipe. You need at least 10 inches of water column with the engine running to operate an LP vapor fueled engine. Because the engine is starving for fuel, its governor opens the throttle to WOT (so it goes to high revs) but there isn't any fuel to make horsepower with so the output voltage falls and the undervoltage alarm trips.
Posted on Dec 03, 2008
I have a Ford LGT with a 14 hp Kohler K321AS engine. Go to Kohler.com and download the service manual for the K321 engine. The manual covers all of the K type engines and gives diagrams and details of all the different types of ignition and electrical systems. It is free. JS
Posted on Jun 07, 2009
The control board that senses load (current) is not working.It should drop to low with no output current. (nothing running)
If you need further help, I’m available over the phone at https://www.6ya.com/expert/craig_3fa289bf857b1a3c
Posted on Jul 07, 2009
Tips for a great answer:
Nov 03, 2015 | Kohler 17RES 17 kW Generator
May 05, 2015 | Kohler Electrical Supplies
Sep 11, 2013 | Kohler Electrical Supplies
Feb 12, 2013 | Kohler 12 kW Emergency Power System -...
Aug 18, 2012 | Kohler Electrical Supplies
Jun 27, 2011 | Kohler 12 kW Emergency Power System -...
Jun 09, 2011 | Kohler Electrical Supplies
May 26, 2010 | Kohler Electrical Supplies
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Apr 13, 2018 | Kohler Electrical Supplies
194 people viewed this question
Usually answered in minutes!