Question about Reddy Heater-170,000 BTU Kerosene Deluxe
Tips for a great answer:
Dec 04, 2016 | Goodman Heating & Cooling
Nov 11, 2013 | Patton Electric Patton PUH680-U Electric...
Feb 13, 2011 | Mr. Heater MHU75NG
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution: You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. Please see "limits, rollout switches & furnace control boards" further down on this page. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 24, 2010 | General Heating & Cooling
Nov 14, 2010 | Goodman Heating & Cooling
Nov 11, 2010 | Heating & Cooling
Mar 14, 2010 | Heating & Cooling
Nov 23, 2009 | Heating & Cooling
Feb 15, 2009 | Goodman GMS90703BXA Heater
201 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: