Question about Goodman CKL24AR24 Air Conditioner
Posted by Anonymous on
I would think the condensor motor bearings are worn. Try testing for end play and side to side play of the condensor motor shaft, with the power disconnected.
Posted on May 05, 2015
SOURCE: I am a ac tech
you aren't an ac tech number one but i shall overlook that . your question is llike will the sun come up in the north or the south tomorrow. obviously in the east as it has since the earth was created. anyway. all compressors since the beginning of time wire up the same .a wire commonly referred to as the common goes from the contactor to the compressor. usually black in color, hence the old coloqualism Blacks are common. the run wire is from the contactor to the run side of the run capacitor or from the contactor to the run connection on the compressor. hence the old slogan reds run when you point a gun at them. the only wire left is the start wire that come from the start capacitor and is usually yellow . hence the old saying blacks are common, reds run, and yellows are always starting something. very ethnic i know but thats how i was taught.now that the wirings correct check to see volts through contactor are correct and if one side of contactor is not feeding. if volts good then check capacitors with a cap checker. if all else looks good kill power and inspect compressor terminals at compressor. if burned off consider a termilock kit good luck..
Posted on Oct 12, 2008
Tips for a great answer:
Oct 09, 2015 | Heating & Cooling
Nov 29, 2014 | Carrier Heating & Cooling
Apr 26, 2011 | Carrier 38CKC042 Air Conditioner
Jan 18, 2010 | Carrier 52PQ307 Wall/Window Air...
Aug 10, 2009 | Heating & Cooling
Jun 25, 2009 | Carrier 38CKC018 Air Conditioner
Jun 17, 2009 | Carrier 36KCARMS Air Conditioner
Apr 26, 2009 | Carrier 38CKC036 Air Conditioner
158 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: