Question about Rheem RHSL-HM2417JA Multi-Position Air Handler - 24,000 BTU, 3 CFM
Wired unit to thermostat and to 2 ton heat pump condenser low voltage r (hot) from condenser to stat to airhandler g (fan) stat to air handler green black. Y (cooling) stat to condenser white or O&B terminal white black w 1 on air handler and blue (L Honeywell stat) to brown (c) condenser and to (C) brown on transformer. blew a 20 amp fuse & had no power to stat. replaced fuse didn't check transformer to see if blown a inline fuse with spade connectors was also installed .I figured transformer was burnt any suggestions??????
Posted by Anonymous on
you can check the inside door chart, and it will map out the led light readout for you. just follow the instructions on the panel and it will tell you possible problems and what you may need to fix to make your unit run correctly.
Posted on Nov 20, 2012
Check for fan operation by turning the fan control at the thermostat to "on". If the fan blows, it works. If not, check a circuit breaker or fuse.
If the fan blows when forcing it on with the thermostat but not in automatic, check the fan control circuit in the air handler. Danger: high voltage, beware! There should be a system wiring diagram inside the air handler somewhere.
Posted on Mar 30, 2014
Tips for a great answer:
May 26, 2014 | Rheem RASL024JEC-RHPNHM2421JC 2 Ton 18.50...
Apr 26, 2013 | Rheem RPQL060JEZ-RHLLHM6024JA 5 Ton 14.5...
Apr 08, 2013 | Rheem 14AJM49A01-RHSLHM4821 4 Ton 14.50...
Nov 18, 2010 | Heating & Cooling
Oct 22, 2010 | Heating & Cooling
Nov 28, 2009 | Heating & Cooling
Jan 05, 2009 | Carrier 38CKC042 Air Conditioner
Nov 10, 2008 | Amana PTH123B25AJ Heat Pump Air...
Jun 15, 2008 | Ruud UBHC Air Conditioner
2,045 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: