Question about Goodman CKL24AR24 Air Conditioner
Posted by Anonymous on
Its normal on a mini split for both lines to be cold. That is why you insulate both lines. The metering device is in the condenser in most mini splits.
Posted on Jun 25, 2012
Tips for a great answer:
Jul 24, 2014 | Goodman Manufacturing Goodman MSG18CWN1W...
Sep 24, 2013 | Amana Heating & Cooling
Aug 14, 2011 | Sanyo 09KHS51 Ductless Mini Split Air...
Apr 28, 2011 | Soleus Mini Split Air Conditioner
Jan 15, 2011 | Goodman Heating & Cooling
Aug 03, 2009 | Goodman CKL24AR24 Air Conditioner
Apr 22, 2009 | Heating & Cooling
First turn the main power off to the unit at the breaker, wait about five min. and switch the breaker back on, then see if this solves the problem. In the instalation manual that came with the unit on the last page you will see a code of the red blinking light, this will tell you the most likely problem if not solved by switching the breaker on again.............Hope this helps
Oct 14, 2007 | Hitachi RAS-09UH Air Conditioner
379 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: