Question about Raypak Pool & Spa
Posted by Anonymous on
SOURCE: lighting the pool heater
You will need to buy a new thermo couple 8.00 part from ace it is the little copper line close to piolet flame,it sences the piolet and allows the gas to open and feed,it is wore out,burned out,replace.
Posted on Mar 30, 2009
this usually indicates a high limit condition.you must first ascertain if you have a component failure or a true high tempature condition.your model has 2 limit controls and they are both located in side panel on water in/out header
Posted on Sep 19, 2009
SOURCE: I have a Raypac digital
Hello my name is Heath it will be my pleasure to assist you. Find the rollout switch and on the back there is a small red button if you push the button in it will reset the switch. The rollout is usually located near the burner section of the heater.I will attach a picture of a rollout switch which shows the small red button.
Posted on Oct 25, 2010
Check the igniter on pilot assembly for soot build up, this igniter also acts as sensor for pilot flame proving, it will detect less heat from pilot flame if there is soot formed on and will not fire up burners. Check also the location of the temperature probe that you have replaced, it may not have sensed correct water temperature. If you think that hi limit is bad, you have to replace it right away because hi limits on all gas fired equipments is the safety device of the system in terms of preventing over heating which could result damage on property or life.
Posted on May 26, 2011
Tips for a great answer:
Oct 11, 2014 | Raypak 2100 Pool Heater Gas 266000 BTU'...
Nov 27, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jul 10, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
May 23, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Jul 05, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
May 24, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
176 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: