Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Electrican wired in 230v to,two air handlers. On a 110v units. Mother boards fryed. I replaced the boards. Only one remote controller was given for two air handlers. system was restarted. It cooled for 20 mins. Then fan cut off and coil started to get frozen. Compressor continued to run. I am going to change the reciver board and get one more remote controller. I think the communition link between the reciver board and fan are not being kept in memorey. Or the fan drops out on over load due to the 230v. If the voltage made it that far before the board got cooked.
Wireing this type AC with the wrong voltage, will damage more than the circuit boards. I think the installer wil need to be responsible for the damage he created. The factory will also try to get out of the replacement because of the installers lack of know how.
Posted on Oct 20, 2007
Tips for a great answer:
Sep 25, 2014 | Heating & Cooling
Jul 18, 2012 | Goodman Heating & Cooling
Sep 19, 2011 | Amana Heating & Cooling
Jul 10, 2011 | Heating & Cooling
Dec 10, 2017 | Goodman Heating & Cooling
Oct 26, 2009 | Heating & Cooling
Oct 16, 2009 | Goodman GMS90703BXA Heater
Aug 10, 2009 | American Standard Heating & Cooling
Oct 09, 2008 | Goodman Heating & Cooling
Jan 05, 2008 | Heating & Cooling
278 people viewed this question
Usually answered in minutes!