Question about Taco 006-B4 1/40 HP Bronze Circulator Pump
My hotwater tank is a storage tank with a coil in my boiler; have a Taco 006 circulator pulling hot water from boiler coil to tank; ran out of hot water today for first time; water feed from boiler is hot to touch; water feed out from tank is tepid; 006 is red hot to touch; how can i test aquastat and/or pump
Posted by Anonymous on
SOURCE: My upstairs air handler is
You have a problem with your fill valve or pressure reducing valve...it is not uncommon for these valves to plug up or fail to work right.... this valve's job is to maintain 12 psi in your system.
If you do not have enough pressure it will not push the water to the upstairs air handler...
You also will then need to get the air out of the pipes for the pump to work right after getting the pressure problem fixed...
Here is a tip that will help you with that also...
Valve Pressure Reducing or Pressure Reducing Valve
Posted on Nov 06, 2010
Tips for a great answer:
Dec 31, 2016 | Water Heaters
Jun 01, 2013 | Water Heaters
Apr 20, 2013 | Dunkirk Q90-75 Quantum High Efficiency...
Oct 05, 2011 | Water Heaters
Nov 04, 2009 | Water Heaters
Sep 03, 2009 | Grundfos RCP-96 Recirculation Pump for...
Aug 09, 2009 | Emerson InSinkErator C1300 Chrome...
Mar 18, 2009 | Water Heaters
217 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: