Question about Freezers
It will work fine the the over load kicks it off after a week if you turn it off then on you can hear the over load click if i leave it off for a few days it will work again for about a week or 2 then do it again took relay and overload off and they look fine and working at this time could it be a bad overload or relay if not should i check the draw of the comp when it acts up and what should the max draw be? thank you
It sounds like the compressor is starting to get a little worn out and needs some assistance starting. This is achieved by adding a start capacitor via a Supco RC0810 3n1 start device.
Posted on Oct 15, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 17, 2013 | Kenmore 20.3 cu. ft. / 575 liter Upright...
Jul 23, 2011 | Freezers
Jun 18, 2011 | Hoover Freezers
Mar 22, 2011 | Freezers
Jul 02, 2009 | Kenmore Freezer 20.3 cu. ft. Frost Free...
Jan 28, 2009 | GE 14.8 cu. ft. / 419 liter Chest Freezer...
Feb 07, 2008 | Freezers
636 people viewed this question
Usually answered in minutes!