Question about Heating & Cooling
Probably a failure of the draft inducer fan motor, draft inducer blower, or the pressure switch that senses the operation of the draft inducer.
Posted on Nov 11, 2013
Turn the power off to the Air handler unit.
Remove the thermostat from the wall, (Just the face part).
Look on the back side of the thermostat and verify that the jumpers are set to electric and not gas, otherwise the fan will not run during heat mode, they come from the factory usually set for gas.
If this is a electric heater this will solve your problem, If it is gas then it will be more detailed. Once you put it back on keep in mind that most thermostats have a 3-5 minute delay so just give it a little time and the fan should then work once you have the jumpers in the correct position.
Thank you for using FixYa!
I’m happy to help further over the phone at https://www.6ya.com/expert/michael_341f3f9dee622e54
Posted on Nov 17, 2009
SOURCE: bryant furnace codes
If you have a Bryant split system, that is gas fired, and you are having a problem with it because of a flashing led, you need to remove the panel to excess the glued on chart that will tell you what the code is according to the amount of flashes its showing you. You may have 2 long flashes and one long, or something different? Look at the chart inside, and it will tell you what is wrong.
A/C, Heating Contractor
Posted on Nov 21, 2010
Tips for a great answer:
Jan 08, 2017 | Bryant Heating & Cooling
Jan 02, 2015 | Heating & Cooling
Nov 28, 2013 | Heating & Cooling
May 08, 2012 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Jan 23, 2011 | Bryant Heating & Cooling
Nov 25, 2010 | Carrier Heating & Cooling
Jun 05, 2009 | GE Zoneline AZ55H07D Air Conditioner
499 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: