Question about Little Giant VCMA-15ULST, 1/50 HP, 65 GPH - Automatic Condensate Removal Pu
These pumps have a float arm inside that tell the pump when to turn on and off, it sounds like your arm is stuck or broken. The top of the unit can be taken off of the reservoir to check for damage.
Posted on Oct 02, 2009
I assume the unit is overflowing, because the pump is not running. Check th hose connection and be sure the line bringing the water into the pump is inserted in the opening. Can you hear the motor run? You can remove the top, and be sure the float switch is working and that the pump inlet is not clogged with debris. Sometimes you'll get mold and dirt mixed with water clogging the inlet. If the motor doesn't run, and the switch works, then it probably isn't worth fixing as you can buy these from 35.00--50.00
Posted on Jul 04, 2010
Tips for a great answer:
Usually answered in minutes!
Step 2: Please assign your manual to a product: